R
base_p
23.04
Ω
=
R
base_s
120 volt
⋅
I
rat_s
:=
R
base_s
1.44
Ω
=
R
wp
0.01 R
base_p
⋅
:=
R
wp
0.23
Ω
=
R
ws
0.01 R
base_s
⋅
:=
R
ws
0.014
Ω
=
Problem 3: A threephase load is drawing 250 kW real power at a power factor of 0.75 lagging.
a) Find the apparent power S drawn by the load in kVA
333.3
.
b) Find the reactive power Q drawn by the load in kVAR
220.5
.
c) Find the capacitor bank rating in kVAR to increase the combined power factor to unity (1.0)
220.5
.
SV
I
⋅
=
PV
I
⋅
pf
⋅
=
QV
I
⋅
sin acos pf
()
⋅
=
SP
2
Q
2
+
=
acos 0.75
(
)
41.41 deg
=
S
P
pf
=
S
250 kW
⋅
0.75
:=
S
333.3 kVA
=
Q
S sin acos 0.75
⋅
:=
Q
220.5 kVAR
=
EE 4343, Test 1, Spring 2002:
Dr. M. Giesselmann, February 13, 2002
Definitions:
freq
60 Hz
⋅
:=
ω
2
π
⋅
freq
⋅
:=
MW
1000 kW
⋅
≡
kVA
kW
≡
kVAR
kW
≡
m
Ω
Ω
1000
≡
MVA
1000 kW
⋅
≡
MVAR
1000 kW
⋅
≡
Problem 1:
a) What is the principal advantage of AC power systems compared to DC power systems?
The ability to step voltages up and down for long distance transmission.
b) Give two solutions to eliminate oscillations of the instantaneous power in AC power systems.
This preview has intentionally blurred sections. Sign up to view the full version.
View Full Document
This is the end of the preview.
Sign up
to
access the rest of the document.
 Spring '08
 GIESSELMANN
 Electric power transmission, Electricity distribution, Threephase electric power, Hz kVAR kW, 60 Hz = Vrms50 50 Hz N A

Click to edit the document details