lecture4

# lecture4 - Zpu = Zactual Zb HV Zpu = j.1 Z actual(HV side =...

This preview shows pages 1–4. Sign up to view the full content.

EE 740 Professor Ali Keyhani Lecture #4 Homework Problems

This preview has intentionally blurred sections. Sign up to view the full version.

View Full Document
Problem 1: A single phase transformer is rated 100MVA, 127/13.2 kV and ten percent leakage reactance. Compute the transformer impedance from the high voltage side. Problem 2: For problem 1, compute the single phase equivalent circuit from the low voltage side. Problem 3: Compute per unit equivalent circuits for the transformers of problem 1 and 2 based on 100 MVA and the rated voltage. Problem 4: Compute the per unit equivalent circuit of problem 3 based on 200 MVA and voltage base of 130 kV on the high voltage side.
Problem 1: A single phase transformer is rated 100 MVA, 127/13.2 kV with 10% leakage reactance. Calculate the transformer impedance from the high side. Solution: j16.129 127 kV 13.2 kV HV LV Rated: 100MVA One phase Eq. Ckt. 127/13.2 kV from high voltage side 10% Sbase = 100 x 10 6 Vb HV = 127 kV Zb HV = (Vb) 2 /Sb = (127 x 10 3 ) 2 / 100 x 10 6 = 161.29

This preview has intentionally blurred sections. Sign up to view the full version.

View Full Document
This is the end of the preview. Sign up to access the rest of the document.

Unformatted text preview: Zpu = Zactual/ Zb HV Zpu = j.1 Z actual (HV side) = j.1 x 161.29 = 16.129 Problem 2: For problem 1 compute the one phase equivalent circuit from the low voltage side. j.17424 Sb = 100 MVA Vb LV = 13.2 kV HV LV Zb LV = (13.2) 2 /100 = 1.7424 Zactual (LV side) = 1.7424 x j.1 = j.17424 One phase Eq. Ckt. from low voltage side Problem 3: Calculate the per unit equivalent circuit of the transformer of problem 1 and problem 2 based on 100 MVA and the rated voltage. Sb = 100 MVA Vb HV = 127 kV Zb HV = 161.29 Zpu HV = Z A / Zb HV = j16.129/161.29 = j.1 pu Sb = 100 MVA Vb LV = 13.2 kV Zb LV = 1.7424 Zpu LV = j.17424/1.7424 = j.1 pu Zpu LV = Zpu HV = j.1 pu j16.129 j.17424 HV LV HV LV 1 φ Eq. Ckt. from HV side 1 φ Eq. Ckt. from LV side 100 MVA 100 MVA 127/13.2 kV 127/13.2 kV HV j.01 LV pu Eq. Ckt. Sb = 100 MVA, Vb HV = 127 kV, Vb LV = 13.2 kV (rated voltage)...
View Full Document

## This note was uploaded on 07/17/2008 for the course ECE 740 taught by Professor Keyhani during the Fall '07 term at Ohio State.

### Page1 / 4

lecture4 - Zpu = Zactual Zb HV Zpu = j.1 Z actual(HV side =...

This preview shows document pages 1 - 4. Sign up to view the full document.

View Full Document
Ask a homework question - tutors are online