This preview shows page 1. Sign up to view the full content.
Unformatted text preview: spectra. Problem 2: We want to install a SVC at load bus to provide reactive compensation consisting of a TCR and 3 capacitor banks (all connected). The compensator must provide 80 MVAr (capacitive) at |V ll | = 13.0 kV and 40 MVAr (inductive) at |V ll | =13.8 kV. a) How much capacitance is needed per capacitor bank (in F)? b) How much inductance must be connected in the TCR? c) Find the RMS current through the TCR for Q=0 at |V ll |=13.2 kV if the capacitors can't be switched out of the circuit. Comment on the results. How about the current if they are switched? d) Implement in ATPDraw and test at the operating limits....
View Full Document
This note was uploaded on 03/19/2010 for the course ECE 529 taught by Professor Johnson,b during the Spring '08 term at Idaho.
- Spring '08