{[ promptMessage ]}

Bookmark it

{[ promptMessage ]}

2010quiz7

# 2010quiz7 - Solution Find Total Enthalpy change for steam...

This preview shows page 1. Sign up to view the full content.

Center for Advanced Energy Systems Michael R. Muller, Director 640 Bartholomew Road, Piscataway NJ 08854 (908) 655-8469 FAX: (732) 445-0730 [email protected] http://caes.rutgers.edu 650:462 Power Plants Quiz 7 NAME: __________________________ Open book November 15, 2010 Consider a single pressure HRSG attached to a gas turbine which exhausts 212 lbm/min into the HRSG at 941°F. If the 15 lbm/min of water at 300 psia enters the HRSG at 100°F and leaves at 700 °F, what are the pinch point temperature difference and the temperature of the air leaving the HRSG? Use Air Tables or Constant Specific Heats – Your choice! BUT – don’t mix them, use either one scheme or the other!!!
This is the end of the preview. Sign up to access the rest of the document.

Unformatted text preview: Solution: Find Total Enthalpy change for steam hin = 68.79 Btu/lbm and hout = 1368.9 Btu/lbm Enthalpy for saturated liquid = 394 Btu/lbm (sat temp = 417.35 °F) Given the flow rate, total energy transfer is: 19,501 Btu/min For air side, with given mass flow rate, total change in enthalpy should be: 91.98 Btu/lbm Inlet enthalpy = 342.9 Btu/lbm Exit enthalpy = 250.95 - exit air temp = 581 °F Pinch Point occurs where water starts to boil. Enthalpy difference there is 1368.9-394 = 974.9 Btu/lbm or 14623 Btu/min For Air – this means a drop in enthalpy of 14623/212 = 68.98 or an enthalpy of 342.9-68.98 = 273.92 Btu/lbm – or a temp of approx 669 °F Pinchpoint = 669-417.35= 251.65 °F...
View Full Document

{[ snackBarMessage ]}

Ask a homework question - tutors are online