This preview shows pages 1–2. Sign up to view the full content.
This preview has intentionally blurred sections. Sign up to view the full version.View Full Document
Unformatted text preview: 5.5 0.8 0.85 Fans 6 2.2 0.8 0.85 Water pumps 3 1.5 0.8 0.85 Heaters 3 7.5 0.85 1.0 Furnaces 3 17.5 0.9 1.0 The lighting load should be calculated as follows. a). Determine the area of all buildings. b). Consider that the lighting load density is 0.15 kW/m 2 c). Multiply the area of all buildings by the lighting load density. You will find the total connected demand of the lighting load. d). Assume that demand factor DF for lighting load is 0.7 e) Calculate the rated demand for the lighting load. 2...
View Full Document
This note was uploaded on 02/16/2011 for the course EE 472 taught by Professor Dr.ilyagrinberg during the Spring '10 term at SUNY Buffalo.
- Spring '10