PROJ1 - 5.5 0.8 0.85 Fans 6 2.2 0.8 0.85 Water pumps 3 1.5...

This preview shows pages 1–2. Sign up to view the full content.

BUFFALO STATE COLLEGE DEPARTMENT OF TECHNOLOGY ENT 472 Power Systems II Course Project Variant 1 Part 1. Load Calculations 1 2 3 4 5 6 Table 1 Name Dimensions Connected Load, kW Demand Factor Power Factor Length (m) Width (m) Building 1 80 40 2500 0.7 0.75 Building 2 80 20 2200 0.72 0.75 Building 3 60 20 480 0.75 0.67 Building 4 40 30 1550 0.7 0.8 Building 5 30 12 * * * Building 6 80 24 880 0.78 0.78 * - See Table 2 Table2

This preview has intentionally blurred sections. Sign up to view the full version.

View Full Document
Name Number of devices, n Real Power, kW Kuf Power Factor Machines 12 5.5 0.3 0.5 Machines 7 3.5 0.3 0.5 Machines 5 1.5 0.3 0.5 Machines 5 0.75 0.35 0.55 Machines 4 0.5 0.35 0.55 Machines 3 1.25 0.35 0.5 Welding machines 8 15.0 0.35 0.55 Cranes 3 7.5 0.5 0.6 Cranes 2 5.0 0.5 0.6 Fans 3 7.5 0.8 0.85 Fans 4
This is the end of the preview. Sign up to access the rest of the document.

Unformatted text preview: 5.5 0.8 0.85 Fans 6 2.2 0.8 0.85 Water pumps 3 1.5 0.8 0.85 Heaters 3 7.5 0.85 1.0 Furnaces 3 17.5 0.9 1.0 The lighting load should be calculated as follows. a). Determine the area of all buildings. b). Consider that the lighting load density is 0.15 kW/m 2 c). Multiply the area of all buildings by the lighting load density. You will find the total connected demand of the lighting load. d). Assume that demand factor DF for lighting load is 0.7 e) Calculate the rated demand for the lighting load. 2...
View Full Document

{[ snackBarMessage ]}

Page1 / 2

PROJ1 - 5.5 0.8 0.85 Fans 6 2.2 0.8 0.85 Water pumps 3 1.5...

This preview shows document pages 1 - 2. Sign up to view the full document.

View Full Document
Ask a homework question - tutors are online