This preview shows pages 1–3. Sign up to view the full content.
This preview has intentionally blurred sections. Sign up to view the full version.View Full Document
Unformatted text preview: Question 1 4 / 4 points When using #6 conductors in an outlet or junction box, each conductor would require a minimum cubic inch allowance for space of ________. 5.0 cu. in. Question 2 4 / 4 points An outlet box with (1) receptacle, (6) #12 circuit conductors and (3) #12 Equipment Grounding conductors would require a box with a minimum cubic inch capacity of _______ . 20.25 cu. in. Question 3 4 / 4 points Where a #12 conductor passes through an outlet box without a splice or termination, the box conductor fill for that conductor would be _____. 2.25 cu. in. Question 4 4 / 4 points Where raceways are used to support a box with a receptacle has two or more conduits with threaded entries and approved threaded hubs, each conduit is required to be supported no further from that box than ______ . 18 in. Question 5 4 / 4 points The minimum required depth of an outlet box that is intended to enclose flush devices is ______....
View Full Document
- Spring '11