This preview shows pages 1–2. Sign up to view the full content.
This preview has intentionally blurred sections. Sign up to view the full version.View Full Document
Unformatted text preview: water removed, in kg, per 1000 m 3 of dry air processed at the entrance to the system. Figure 1 2 3-A wet cooling tower is to cool 60 kg/s of water from 40 to 26 C. Atmospheric air enters the tower at 1 atm with dry and wet-bulb temperatures of 22 and 16 C, respectively, and leaves at 34 C with relative humidity of 90 percent. Using the psychometric chart determine a) The volume flow rate of air into the cooling tower. b) The mass flow rate of the required makeup water. Figure 2...
View Full Document
This note was uploaded on 05/16/2011 for the course ENGINEERIN 366 taught by Professor Oz during the Spring '10 term at Yeditepe Üniversitesi.
- Spring '10