This preview shows page 1. Sign up to view the full content.
Unformatted text preview: or according to the equipments original rating (Name plate & Specification) Note (1) If any equipment is connected with plug point equipments load or plug point rating whichever is maximum shall be taken. In such case, load of plug point shall not be counted separately. (2) For commercial light & fan consumer load of every bulb shall be taken as 100 Watt. (3) The load for Arc/induction furnace shall be worked out on the basis of 600 KVA per ton of the capacity of the furnace. (4) The higher rating of only one equipment shall be considered if both geyser and Air-conditioner (without heater) are installed....
View Full Document
- Spring '07