This preview has intentionally blurred sections. Sign up to view the full version.
View Full DocumentThis preview has intentionally blurred sections. Sign up to view the full version.
View Full DocumentThis preview has intentionally blurred sections. Sign up to view the full version.
View Full DocumentThis preview has intentionally blurred sections. Sign up to view the full version.
View Full DocumentThis preview has intentionally blurred sections. Sign up to view the full version.
View Full DocumentThis preview has intentionally blurred sections. Sign up to view the full version.
View Full Document
Unformatted text preview: Power Systems I l Overhead Conductor l Overhead Spacer Cable l Underground Cable l ThreeConductor Cable l Service Cables Transmission Lines Power Systems I Overhead Conductors l ACSR Aluminum Conductor with inner Steel Reinforced strands l ACAR Aluminum Conductor with inner Al allow Reinforced strands l ACSR/AW Aluminum Conductor with inner Alumoweld Steel Reiforced strands l Aluminum  current carrying member l Steel  structural support Power Systems I Overhead Cable l Where conductor closep roximity is required l Insulating jacket surrounds each conductor l Plastic spacers keep conductors from coming in contact with one another Power Systems I Cables Power Systems I Cables l Underground transmission and distribution cables l Semiconducting material surrounds the conductor to grade the electric field l Plastic jacket provides insulation and protection l Neutral strands for an outer shell for protection and return currents Power Systems I Transmission Line Parameters l Line resistance u dc resistance u ac resistance n skin effect n at 60 Hz: l Temperature effects u increased resistance at conductor temperature rises u wiring is rated for 65 ° C, 75 ° C, or 90 ° C u ambient temperature is 20 ° C A l R dc ρ = dc ac R R ⋅ = 02 . 1 C 228 ° = + + = Al old new old new T t T t T R R ρ = conductor resistivity l = conductor length A = conductor cross sectional area Power Systems I Review of Magnetics and Inductance Ampere’s circuital law ∫ Γ = ⋅ = e i d F l H i e H Γ = H = Magnetic Flux Integral of the flux density that is normal to a defined area ∫ ⋅ = = A d a B H B φ μ B A B = A = φ Integral of the scalar product of a closed path and the magnetic field equals the encircled current Power Systems I Review of Magnetics and Inductance Flux Linkage ∑ = = N i i 1 φ λ Inductance I d I d I I L ∑ ∫ ∑ ∫ ∑ ⋅ = ⋅ = = = a H a B μ φ λ Power Systems I Inductance of a Single Conductor l Conditions: u infinite straight wire is an approximation of a reasonably long wire l Assumptions: u Image the wire to close at +/ infinity, establishing a kind of “oneturn coil” with the return path at infinity u Straight infinitely long wire of radius r u Uniform current density in the wire. Total current is I x u Flux lines form concentric circles (i.e. H is tangential) u Angular symmetry  it suffices to consider H x Power Systems I Inductance of a Single Conductor l General: l Case 1: Points inside of the conductor ( x < r ) x I H I dl H x x x x π π 2 2 = ⇒ = ⋅ ∫ 7 3 4 3 4 2 2 2 2 2 2 2 10 5 . 8 8 2 2 2 2 2 − × = = → = = = = = → = = = → = → = ∫ ∫ π μ π μ π μ λ λ π μ φ λ π μ φ π μ π π π int r x r int x x x x x x x L I x d x r I d dx x r I d r x d xdx r I dx B d x r I B x r I H x I r I Power Systems I Inductance of a Single Conductor l Case 2: Points outside of the conductor ( x > r ) 1 2 7 1 2 ln 10 2 ln 2 1 2 2 2 2 2 1 2 1 D D L D D I x d x I d dx x I d d dx x I dx B d x I H B I I ext D...
View
Full
Document
This note was uploaded on 10/13/2011 for the course EEL 4213 taught by Professor Thomasbaldwin during the Spring '11 term at FSU.
 Spring '11
 THOMASBALDWIN

Click to edit the document details