Split_00054 - 8.74 (contd) Energy balance on...

This preview shows page 1. Sign up to view the full content.

8-54 8.74 (cont’d) Energy balance on cooler-reheater References : Same as Fig. 8.4-2 [including H 2 O(l, 32 o F)] Substance in in ˆ mH ± out out ˆ ± Fresh air feed 10.93 45.5 DA m in lb dry air/min m ± Recirculated air feed 65.57 26.2 air m ˆ in Btu/lb dry air H Delivered air 76.5 21.4 2 HO ( l ) m in lb /min m ± Condensed water (49 o F) 0.165 17.0 2 ( l ) m ˆ in Btu/lb H ii out in 575.3 Btu 60 min 1 ton cooling ˆˆ 2.9 tons min 1 h -12,000 Btu/h QH m H m H =Δ = = = ∑∑ ± ± ±± Percent saved by recirculating = (9.1 tons 2.9 tons) 100% 68% 9.1 tons ×= Once the system reaches steady state, most of the air passing through the conditioner is cooler than the outside air, and (more importantly) much less water must be condensed (only the water in the fresh feed). c. Total recirculation could eventually lead to an unhealthy depletion of oxygen and buildup
This is the end of the preview. Sign up to access the rest of the document.

This note was uploaded on 01/07/2012 for the course CH E 210 at Pennsylvania State University, University Park.

Ask a homework question - tutors are online