This preview has intentionally blurred sections. Sign up to view the full version.View Full Document
Unformatted text preview: total head. Complete with one gallon 3.8 liter polystyrene tank with pump and automatic float control. 1 / 5 hp, 120 V, one phase, 60 Hertz. 2. Condensate piping shall be Type M copper or Schedule 40 PVC. 3. Approved Products-a. No. CU551UL by Beckett Pumps, (888) 232-5388 www.beckettpumps.com b. No. VCL45S by Little Giant Pump Co, Oklahoma City, OK (405) 947-2511 www.lgpc.com PART 3 EXECUTION 3.1 INSTALLATION A. Condensate Drains 1. Support piping and protect from damage. This paragraph pertains to the standard 90 percent efficient furnaces. 2. Do not combine PVC condensate drain piping from furnace combustion chamber with copper condensate drain piping from cooling coil. END OF SECTION...
View Full Document
- Winter '08
- UCI race classifications, Tour de Georgia, American Society for Testing and Materials, Little Giant Pump Co, drain piping, drain piping systems