Unformatted text preview: UFO-5 by Dual-Lite Inc, Cheshire, CT (203) 699-3000 www.dual-lite.com d. I-48 by Iota Engineering Co, Tucson, AZ (520) 294-3292 www.iotaengineering.com e. PS600C by Lithonia Lighting, Conyers, GA (770) 922-9000 www.lithonia.com f. Equal as approved by Architect before bidding. See Section 01600. PART 3 EXECUTION 3.1 INSTALLATION A. Install fluorescent emergency lighting pack in ballast channel with charging indicator light and test switch mounted on fixture end, or visible and accessible through lens. B. Wire so unit can be tested with lights on. C. Wire so lamps in normal mode are switched off with other lighting in area. Connect emergency lighting unit to unswitched conductor of normal lighting circuit. END OF SECTION...
View Full Document
- Winter '08
- Light, Rechargeable battery, Lithonia Lighting, fluorescent emergency lighting