This preview has intentionally blurred sections. Sign up to view the full version.View Full Document
Unformatted text preview: - Telephone jacks and plates 4. Telephone Company - Furnish and install main service cable. PART 2 PRODUCTS 2.1 COMPONENTS A. Telephone outlet box shall be single device outlet box . B. Building Telephone System Cable 1. CAT 5E, 24 AWG, solid bare copper, four pair, UTP. 2. Meet requirements of EIA / TIA 568 Standard. PART 3 EXECUTION 3.1 INSTALLATION A. Install main service raceway as directed by telephone company. Leave pull wire in raceway. B. Install cable from terminal board to each telephone outlet unless indicated otherwise on Drawings. C. Terminate cables at each outlet with specified modular telephone jack assembly. D. Leave adequate slack cable at terminal board for termination of each cable run. END OF SECTION...
View Full Document
- Winter '08
- Twisted pair, telephone system, main service raceway