This preview shows page 1. Sign up to view the full content.
Unformatted text preview: pressure. It may be connected to
the steam space or to the steam connection to the water column. 7.11 Whenever repairs/replacements are made on fittings or appliances, the work shall comply
with the section on New Installation of the Philippine Medical Engineering Code. 7.12 After a permit has been granted to install a boiler/pressure vessel/pressurized water heater
upon payment of the installation fees thereof, it shall be the duty of the Building Official
to make periodic inspection of the installation to determine compliance with the approved
plans and specifications. 7.13 Upon the completion of the installation, the Building Official shall conduct an inspection
and test, after which a certificate of operation for a period not exceeding one year shall be
issued upon payment of the required inspection fees. 7.14 The Building Official shall notify the owner in writing of the intended date of the annual
inspection at least 15 days in advance. However, the owner may request a postponement
in writing of said inspection and the Building Official shall fix a date for inspection
agreeable to both, but not to exceed 30 days from the intended date. 7.15 The owner or user of a boiler shall prepare the same for inspection by cooling it down,
blanking off all connections to adjacent boilers, removing all soot and ashes from tubes,
heads, shell, furnace and combustion chamber. the owner shall assist the Building
Official by providing all labor and equipment required during said inspection. 8. Refrigeration and Air Conditioning:
8.3 The temperature and humidity of the air to be used for comfortable cooling shall be
maintained at 68-74°F effective temperature at an air movement from 4.57 to 7.60 MPM
within the living zone.
Water from evaporators, condensers and other machinery shall be properly collected into
a suitable water or drainage system.
Ducts shall be constructed entirely of non-combustible materials such as steel, iron,
aluminum or other approved materials. Only fire retardant lining shall be used on the
inside of ducts. 8.4 Access doors shall be provided at all automatic dampers, fire dampers, thermostats and
other apparatus requiring service and inspection in the duct system. 8.5 Where ducts pass thru walls, floors or partitions, the space around the duct shall be sealed
with fire resistant material equivalent to that of the wall, floor or partition, to prevent the
passage of flame or smoke. 8.6 When the ducts or the outlets or inlets to them pass through fire walls, they shall be
provided with automatic fire dampers on both sides of the fire wall through which they
pass. 8.7 Fire doors and fire dampers shall be arranged to close automatically and remain tightly
closed, upon the operation of a fusible link or other approved heat actuated device,
located where readily affected by an abnormal rise of temperature in the duct. 8.8 Each refrigerating system shall be provided with a legible metal sign permanently
attached and easily accessible, i...
View Full Document
This note was uploaded on 09/22/2013 for the course ARIDBE AR taught by Professor Any during the Fall '12 term at Mapúa Institute of Technology.
- Fall '12