Unformatted text preview: blishments manufacturing photographic films and their storage
incidental thereto and films stored or being used in standard motion picture booths.
(b) Photographic X-ray film may be identified by the marking on the edge of the film.
SECTION 1403. Fire Extinguishing System
Unless otherwise provided in this Code, all fire extinguishing systems when so required shall be
of a type, specifications, and methods of installation as prescribed in accordance with the requirements
of the Secretary. CHAPTER 15 PRE-FABRICATED CONSTRUCTION SECTION 1501. Prefabricated Assembly
(a) Prefabricated assembly is a structural unit, the integral parts of which have been built up or
assembled prior to incorporation in the building.
(b) The Secretary shall prescribe special tests to determine the structural adequacy, durability,
soundness, weather and fire resistance of prefabricated assemblies.
(c) Every device or system to connect prefabricated assemblies shall be capable of developing the
strength of the different members as an integral structure, Except, in the case of members forming part of
a structural frame as specified in this Code. Anchorages and connections between members and the
supporting elements of the structure or walls shall be capable of withstanding all probable external and
internal forces or other conditions for a structurally adequate construction. In structural design, proper
allowances shall be made for any material to be displaced or removed for the installation of pipes,
conduits, or other equipment.
(d) Placement of prefabricated assemblies shall be inspected to determine compliance with this
Code. CHAPTER 16
PLASTICS SECTION 1601. Approved Plastics
Approved plastic materials shall be those which have a flame-spread rating of 225 or less and a
smoke density not greater than that obtained from the burning of untreated wood under similar
conditions when tested in accordance with generally accepted engineering practices. The products of the
combustion shall not be more toxic than the burning of untreated wood under similar conditions.
SECTION 1602. Installation
(a) Structural Requirements – All plastic materials shall be of adequate strength and durability to
withstand the prescribed design loads. Sufficient and substantial technical data shall be submitted to
establish stresses, maximum unsupported spans, and such other information as may be deemed necessary
for the various thickness and forms used.
(b) Fastenings – Fastenings shall be adequate to withstand design loads and internal and external
stresses required of the assembly. Proper allowances of plastic materials in conjunction with other
materials with it is assembled or integrated shall be provided. SECTION 1603. Glazing of Openings
(a) Doors, sashes and framed openings in exterior walls of all buildings except Types IV and V
Constructions may be glazed or equipped with approved plastics: Provided, that:
(1) The wall in which such glazing is installed is so located that openings are not r...
View Full Document
This note was uploaded on 09/22/2013 for the course ARIDBE AR taught by Professor Any during the Fall '12 term at Mapúa Institute of Technology.
- Fall '12