This preview shows page 1. Sign up to view the full content.
Unformatted text preview: ons, it shall provide a positive seal within the manufacturer’s recommended range of maximum joint deflection. Not more than two splices in each ring shall
be permitted. 10 SPECIALS
10.1 Fabrication 12 WORKMANSHIP AND FINISH The steel for fabricated steel plate specials, is cut,
shaped and welded so that the finished special has the
required shape and internal dimensions. Adjacent segments are jointed by butt welding. Before lining and
coating, the welding of specials shall be tested by use
of hot oil or dye penetrant according to IS 3658 and
defects, if any shall be rectified. The steel plate thickness for specials shall be as given in IS 1916. 12.1 Deviation from the Straightness
When measured by means of a one metre straight edge
the deviation from straight per metre length shall not
exceed 5 mm.
Pipe shall be free from local depressions or bulges
greater than 5 mm extending over a length, in any
direction, greater than twice the thickness of barrel.
The external surface of the pipe may be sand faced,
when coating of cement mortar is applied. In die penetration test, a white wash is applied over
the weld on one side of the cylinder; on other side
when coloured paraffin or similar product is applied
over the weld, no coloured spot shall appear on the
whitewash before 4 h. If any coloured spots appear
before 4 h, weld shall be repaired and retested. 13 TEST
13.1 Design Proving and Manufacturing
Approval Test in Factory 10.2 Lining and Coating
Steel plate specials are lined and coated with concrete
or cement mortar or other approved materials, as
agreed between the manufacturer and the purchaser.
The proportion of cement to total aggregate shall not
be leaner than 1:3 by mass. Process As Won os 4 to 5 pipes are made, these shall be installed and site pressure test shall be conducted, to prove
and finalize pipe and joint design and joint dimension
tolerances, etc. For one diameter and different pressure, only the test for highest pressure shall be done.
For this test no external load shall applied. 10.3 Reinforcement
For concrete or cement mortar coating, reinforcement
shall be suitably tack welded to the shell. The reinforcement shall be wire rods and spirals or wire mesh
or wire fabric. 13.2 Hydrostatic Factory Test
The pipe shall be tested in accordance with IS 3597.
The pipe must not show leakage. Damp or wet patches
shall be accepted. If the pipe fails to pass the test, it
can be cured or repaired to improve its water tightness and then retested. In case the pipe does not stand
the rated internal pressure, it shall be accepted for
lower pressure, purchaser at his own discretion may
accept the pipes for lower pressure to which it withstands, provided all other requirements are conforming to this standard. 10.4 Jointing Between Special and Pipe
The special shall be jointed to the pipe by same robberring joint as for pipes or by caulking with mortar.
For this purpose steel collars shall be welded to steel
specials to allow caulking o...
View Full Document
This document was uploaded on 10/01/2013.
- Fall '13