This preview shows page 1. Sign up to view the full content.
Unformatted text preview: ult, gathering data on individual process equipment was, by and large,
not supported by the sub-metering data collection system. At the time of arrival at the facility, use -usain1 -usato3
Machine A Machine B Machine C Bus3 Machine D Figure 4-1: The simplified electricity distribution tree for the IADC as shown in Figure 2-6 with
shaded boxes indicating sub-meter locations.
of the ION EEM system was limited. The facility Energy Champion would track electricity usage of
the overall facility over time using the system, and email weekly reports to department-level Energy
Champions that included key metrics such as cumulative percentage increase/decrease of electricity
use versus the same date the previous year, and energy usage trends for each substation. While this
approach provided some visibility into the overall trends of electricity use in the facility, the value of
the information, especially to manufacturing employees, was limited due to the fact that there was
no direct relationship between energy usage at the substation level and for individual departments
and cells. In general, no...
View Full Document
This document was uploaded on 03/03/2014 for the course ADMIN 1 at Universidad Nacional de Colombia.
- Spring '14