Figure ## Phillips RC486B W62L62 VPC 1xLED78S/TWH-6700 AC-MLO Luminaire RC132V W30L60 PSU 1 xLED18S/840 NOC Light Output Ratio 99.90% Lamp Luminous Flux 4300 lm Luminaire Luminous Flux 4296 lm Power 45.0 W Luminous Efficacy 95.5 lm/W Colorimetric Data *copy sa nighttime floor report* Table ## Phillips RC486B W62L62 VPC 1xLED78S/TWH-6700 AC-MLO – Datasheet Figure ## Phillips RC486B W62L62 VPC 1xLED78S/TWH-6700 AC-MLO – Polar Intensity Diagram This luminaire was used due to it’s higher luminous flux and wide distribution curve. This resulted to a larger area being able to reach the standards of the room. Figure ## Phillips RS060B 1Xled5-36-/830 Luminaire RC132V W30L60 PSU 1 xLED18S/840 NOC Light Output Ratio 99.67% Lamp Luminous Flux 480 lm Luminaire Luminous Flux 478 lm Power 6.0 W Luminous Efficacy 79.7 lm/W
UST: EE524L-T2AY1920-5EEB-G6 13 Colorimetric Data *copy sa nighttime floor report* Table ## Phillips RS060B 1Xled5-36-/830 – Datasheet Figure ## Phillips RS060B 1Xled5-36-/830 – Polar Intensity Diagram This luminaire was used as an entry or exit light for the door for the person inside or going inside have visual of the area around the door. It was also chosen for its small distribution curve in order to lessen the overlapping of lighting at certain areas. Figure ## Sacristy Luminaire – Light Distribution Curve Figure ## Sacristy – Luminaire Control Utilizing a three-gang switch, three groups of luminaires can be controlled depending on time and conditions. Luminaire group one consists of luminaire numbers one, five, six and three. They are primarily used during the night as the areas they are located are reached by the sunlight during the day. Luminaire group 2 controls luminaire 2 and 4 and can be used during the day and night as the areas they are located far from the windows. Luminaire group 3 controls luminaire 7 which is used at day and night as sunlight reaching the couches are not enough. c. Daytime Data Figure ## Sacristy – Daytime – 3D Render 1 Figure ## Sacristy – Daytime – 3D Render 2 Figure ## Sacristy – Daytime – Room – False Color 1 Figure ## Sacristy – Daytime – Room – False Color 2 i. Working Plane 1 3 5 6 2 7 4
UST: EE524L-T2AY1920-5EEB-G6 14 Figure ## Sacristy – Daytime – Working Plane – Combined Data 1 Figure ## Sacristy – Daytime – Working Plane – Combined Data 2 The simulation was done under average sky conditions at 12 noon with luminaire groups two and three turned on. The room was able to obtain an average illuminance value of 338 lux, meaning the room was able to reach its standard of 300 lux. Uniformity with the light distribution was also observed in the important areas such as where the chairs are located and the table where preparations for the mass is made. Small pockets of lower illuminance were present in the corners, but they can be said as areas with little to no activities due to their location and size. Lower values can also be seen in the doors to the side, but it is meant to aid the eyes of the person going in to gradually adjust to the amount of light in the room.
You've reached the end of your free preview.
Want to read all 25 pages?
- Spring '18
- Kenneth Sinson
- ii. Floor Plane, luminaire group