VENT TERMINATIONVSTR shall terminate vertically not less than 150 mm above the roof nor less than 0.3 meter from any vertical surface nearby.
VENT TERMINATIONEach vent opening shall terminate;•Not less than three (3) meters from any openable window•Not less than 0.9 meter above any openablewindow•Not less than 0.9 meter above any lot line , alley, and street boundary line.
VENT TERMIINATIONVertical vent pipes shall extend 3.00 m distant from any part of the roof that is used for human activities and shall extend not less than 2.10 m above such roof.
VENT TERMINATIONFlagpoling of vent is prohibited.
VENT TERMINATIONJoint at the roof around stack unit pipes shall be made watertight.
RELIEF VENT AND YOKE VENT10TH FLOOR•Each soil or waste stack which extends ten (10) or more stories above the building drain shall be served by a parallel vent stack . It shall connect to the soil or waste stack at ground level and at every fifth floor levels with a “yoke vent"