Equipment ratings for the five-bus power system shown below are as follows:

Generator G1: 50 MVA, 12 kV, X" = 0.2 per unit

Generator G2: 100 MVA, 15 kV, X" = 0.2 per unit

Transformer T l: 50 MVA, 10 kV Y/138 kV Y, X = 0.10 per unit

Transformer T2: 100 MVA, 15 kV Δ/138 kV Y, X = 0.10 per unit

Each 138-kV line: X1= 40 Ω

A three-phase short circuit occurs at bus 5, where the pre-fault voltage is 15 kV. Pre-fault load current is neglected.

(a) Draw the positive sequence reactance diagram in per-unit on a 100 MVA, 15-kV base in the zone of generator G2. Determine: (b) the Thevenin equivalent at the fault, (c) the subtransient fault current in per unit and in kA rms, and (d) contributions to the fault from generator G2 and from transformer T2.

### Recently Asked Questions

- Let random variable x represent the number of heads when a fair coin is tossed three times. (a) Construct a table describing the probability distribution.

- Please refer to the attachment to answer this question. This question was created from Ch12.

- Please help. Mimi has eight books from the Statistics is Fun series. She plans on bringing two of the eight books with her in a road trip. (a) Does the order