View the step-by-step solution to:

# Equipment ratings for the five-bus power system shown below are as follows: Generator G1: 50 MVA, 12 kV, X" = 0.2 per unit Generator G2: 100 MVA, 15...

Equipment ratings for the five-bus power system shown below are as follows:

Generator G1:         50 MVA, 12 kV, X" = 0.2 per unit

Generator G2:        100 MVA, 15 kV, X" = 0.2 per unit

Transformer T  l:     50 MVA, 10 kV Y/138 kV Y, X = 0.10 per unit

Transformer T2:    100 MVA, 15 kV Δ/138 kV Y, X = 0.10 per unit

Each 138-kV line:  X1= 40 Ω

A three-phase short circuit occurs at bus 5, where the pre-fault voltage is 15 kV. Pre-fault load current is neglected.

(a) Draw the positive sequence reactance diagram in per-unit on a 100 MVA, 15-kV base in the zone of generator G2. Determine: (b) the Thevenin equivalent at the fault, (c) the subtransient fault current in per unit and in kA rms, and (d) contributions to the fault from generator G2 and from transformer T2.

### Why Join Course Hero?

Course Hero has all the homework and study help you need to succeed! We’ve got course-specific notes, study guides, and practice tests along with expert tutors.

### -

Educational Resources
• ### -

Study Documents

Find the best study resources around, tagged to your specific courses. Share your own to gain free Course Hero access.

Browse Documents